Michael Phelps 9 Hot Tub
Quite possibly the biggest and most spacious hot tub available anywhere on the planet.
Finance £238,78 pcm
Key Hot Tub Features
Hot Tub Overview
The Michael Phelps 9 hot tub comes with an insulating spa cover, cover lifter, steps, a complete spa water care kit and water testing starter kit. The Michael Phelps 9 hot tub has a 10 years full structural warranty, 5 years component and 5 years no leak plumbing warranty and 7 days technical support. Full nationwide delivery and installation is available on this hot tub, along with affordable hot tub finance options. Please do contact us if you have any other questions.
Michael Phelps 9 Specifications and Technical Details
Hot Tub Seating
Jets, Pumps & Components
Weights & Dimensions
Delivery & Installation Requirements
Please check and double check the access route. If you have any concerns or considerations please don’t hesitate to call us. We have vast experience in hot tub installation however good preparation is always a good idea.
Michael Phelps 9 Electrical Requirements
40AMP ELECTRICAL REQUIREMENTS. (MICHAEL PHELPS MODELS 7,8,9)
A 40 amp supply using 6mm steel wired armoured cable with local isolation via rotary isolator, terminated with a 7 metre tail. A 40 amp breaker is required. The supply should feed directly from a suitable source (typically your domestic fuse box) to the rotary isolator which is typically mounted 2 metres from the spa area. A 7 metre ‘tail end’ is required from the isolator to the spa – the tail is ‘hard wired’ to the spa by our engineers. Please note; the long tail is required to allow perfect siting and orientation of the spa. If the cable distance is longer than 20 metres, a 10mm SWA cable will be required – Please double check this with your electrician.
A 40AMP dedicated electrical installation will typically cost around £300-£350 and take no more than a couple of hours to complete.
NOTE: THE 40 AMP SUPPLY ABOVE WILL REQUIRE YOUR ELECTRICIAN ON-SITE DURING THE INSTALLATION TO COMPLETE THE HARD WIRED CONNECTION.